Sign up here to join the SIAFOS Woodstock group
Woodstock classrooms need more filtration capacity
Even with the Intellipure air purifiers running at their tolerable noise level (half speed):
✘ Classroom with the lowest airflow: 3a – One of the kindergarten rooms
1.4 air changes per hour*
With ventilation & filtration this low, how long do kids’ and staff’s viruses in their respiratory aerosols linger in these kindergarteners’ air?
>1 hour and 46 minutes
At 1.3 air changes/hour, 1 hour 39 minutes is how long it takes for the HVAC system and Intellipure to clear out 90% of the respiratory aerosols being produced when kids and staff breathe, talk, sing, cough and sneeze.
Furthermore the HVAC system portion of this far too low ventilation rate is solely from an exhaust fan in the room’s closet. There is no air supplied to the classroom by a proper HVAC system.
✘ 1 more Woodstock classroom has less than 2 air changes per hour – it’s the other kindergarten room
Room 2a has 1.6 air changes per hour. At that rate, it takes the HVAC system and Intellipure 1 hour and 26 minutes to clear 90% of the respiratory aerosols from this second class of kindergarteners’ classroom air.
This kindergarten room is likewise only provided actual ventilation from an exhaust fan in the closet.
✘ 11 classrooms are between 2 and 3 air changes per hour & 18 more are between 3 and 5 – all below recommendations
No classrooms at Woodstock have sufficiently safe air provided by PPS — no classrooms have ventilation and filtration providing 6 air changes per hour or more, clearing 90% of aerosols out in 23 minutes or less.
No classrooms are even above 5 air changes per hour. Let alone classrooms that are even better by providing closer to 12 air changes an hour, where aerosols would clear out by 90% in under 12 minutes.
The 11 Woodstock classrooms that are between 2 and 3 air changes per hour – their HVAC system and Intellipure let aerosols linger for over 45 minutes. And the 18 classrooms between 3 and 5 let aerosols linger for at least half an hour.
About these ventilation and filtration measurements
Before resuming in-person learning in 2021, PPS had airflow testing conducted in every room of every PPS building. We have corrected gaps in Woodstock’s airflow report as originally published by the district, to get this summary. We have also run numbers on one potential plan for Woodstock adding Medify units that are being offered to schools by the Oregon Health Authority, if district personnel follow through on signing up to get them by April 28.
The Intellipure air purifiers are insufficient in Woodstock classrooms
An Intellipure running at its tolerable noise level only provides 182 cubic feet of clean air per minute. Even at its highest speed setting, which is too noisy, an Intellipure only provides 270 cubic feet of clean air per minute.
Woodstock classrooms need additional, high quality air purifiers to provide safe air to kids now, when HVAC system overhauls will take the district years to do in all schools.
PPS staff need to order additional air purifiers for Woodstock from the Oregon Health Authority by April 28
The Oregon Health Authority first opened this program at the beginning of April, and at that time, PPS planned to order “no additional units.” But parents like you across our district organized with us to help district staff and leaders understand the need to take full advantage of this opportunity to obtain better air purifiers at no cost to PPS. The district announced initially that they would order only 600 units, but we have over 2600 classrooms in the district.
Parents in our network stepped up again, and our work paid off! PPS announced that they have placed an order for 3500 air purifiers.
We will see for sure how many of which models each school will get when the orders arrive, but we expect this to result in each classroom in the district either having two Medify air purifiers or one Intellipure and one Medify air purifier. And we hope the order will include the MA-1000s for gyms, cafeterias, large libraries, large music rooms and performance rooms, and other large communal spaces that serve students and staff. With both an Intellipure and a Medify, teachers can set the two air purifiers at a quiet speed, but still get more clean air delivered to the room than one Intellipure can deliver, even when it is set at it’s highest setting!
We’re not done working for cleaner classroom air, though. You can still join us below to learn more!
Our analysis looks at what Medify’s would accomplish for ACH values across rooms at Woodstock, if added to Woodstock according to OHA’s guidelines from the webinar for this program.
Highlights of our preliminary classification of providing Medify’s to Woodstock using OHA’s suggestions for how to distribute them
2 Medify MA-50’s, 34 Medify MA-112’s, and 4 Medify MA-1000’s would:
- Bring 30 out of 31 Woodstock classrooms to above 3 air changes an hour (although one of the kindergarten classrooms would still below 3, at 2.8 air changes per hour)
- Bring the library up from 2.6 to 4.1 air changes each hour, if the library is provided the powerful MA-1000 set at it’s quiet speed
- Bring the cafeteria up to 7.6 air changes per hour
- Bring the large gym and the large aftercare room up to 3.2 and 3.6 air changes an hour, respectively
- Have classrooms ranging from 2.8 to 7.4 air changes per hour
Join us in asking PPS and OHA to add these new filters while also maintaining the existing filtration capacity the Intellipures provide.
How can you help?
We need to make sure PPS and OHA provide more air purifiers to Woodstock – Sign up to help advocate for PPS ordering these units and OHA granting them!
Let’s get more air filtration in the 13 Woodstock classrooms that do not even get 3 changes of air per hour and the 18 classrooms that only get between 3 and 6! And let’s make sure Woodstock’s cafeteria, where kids pack in close to eat lunch, and library and other key spaces get better air quality.
Join us to be part of a group of parents and community members advocating for strategic, effective, and science-based planning for sufficient ventilation and filtration capacity in PPS schools — including Woodstock.
Sign up on our signup form to also help make a better proposed plan for Woodstock. Facilities staff worked hard to get the Intellipures, but PPS left serious gaps in the ventilation and filtration in elementary, middle school, and K-8 schools across the district.
So we would like participation and feedback from more PPS community members – parents, family, and actual staff in our schools – on what spaces in each school are actually used for what, so that PPS kids and staff, including kids and staff at Woodstock, get more of the quiet, effective filtration capacity that they need. Sign up below to join our organizing for PPS air quality!
*Notes on our numbers
Air changes per hour given here are “equivalent” and include ventilation and filtration. These numbers are based on the district’s airflow report for Woodstock, conducted in August 2021 (available at tinyurl.com/woodstockairflow) but corrected using specifications from the manufacturer of the Intellipure units to allow calculation of air changes per hour with the Intellipure at half speed instead of the district-provided air changes per hour with the Intellipure set at full speed.
Also, please note that the total classrooms across the district below 3 and between 3 and 6 are 597 / 1111 and counting…